Specifying Pipes in PMS involves indication of following information.
Size range specified will be as per Concerned Spec Purpose and Type of Pipe Construction such as Seamless or Welded.
Pipe can be Seamless for upto 24″. Higher sizes can be welded e.g. ERW or EFW depending of Material of Construction.
Radiography will be specified as per applicable code for the concerned piping system. e.g. ASME B36.3.
e.g. : 100# RX (Only for Welded Pipes)
Material of Construction
Choice of piping material depends on temperature and fluid properties.
E.g. Material : ASTM A106 Gr. B Seamless, A672 Gr. B65 Cl.42 for EFW etc.
Pipe End Type
Pipe end type depends on Pipe Size and Fittings End Type. Small bore piping is Socketwelding or Threaded. Big Bore piping Buttwelded.
Ends : Plane End for small bore, Bevelled End for Big Bore
Dim Standard : ASME B36.10 for CS Pipe, ASME B36.19 for SS Pipe
Pipe thickness is calculated as per applicable piping code such as ASME B36.3. Based on calculated size, standard pipe thickness is chosen from pipe dimensional standard specified as above. Thicknesses for all applicable pipe sizes is specified in separate chart in Piping Material Specification.
Example Chart :